Card Set Information
AIR advanced systems
Cooling water supplies for instrument air compressor after coolers?
-critical service water
-non critical service water
Purpose of high pressure air system?
Safety related portion of the system provides high pressure control air for operation of vital valves located in each of the engineered safeguards rooms.
Non safety related portion provides high pressure control air for operation of non vital valves in the turbine building.
CV-1221 " Service/instrument air tie in from the FWP building"
Isolation between instrument air/FWP air
Operated by control switch in CR
No auto functions
Fails open on a loss of air/DC bus D-11
Service air header supplies?
Cooling tower level (M/U basin) instrumentation bubblers
Control air to fire protection deluge systems
Spent resin storage and ALPS
Air to P-972 "pumping trap for E-57 condensate"
-SIRWT HX trap
Purpose of FWP air?
Non safety related and independent air system providing filtered, moisture-free air to feedwater building components
Also can supply filtered, dried air directly to the instrument and service air system.
Instrument air compressor starts?
--compressor starts up
--microprocessor controls load/unload
--load at 95 psig, unload at 105 psig
-in auto, starts on low header pressure of 92 psig
Instrument air prefilters F-12A/B max D/P?
Minimum T-9A/T-9B, high pressure air tanks, pressure in Modes 1,2,3 >/= 325F.
>/= 260 psig
Instrument air compressors C-2A, C-2B, C-2C
Air cooled rotary screw type compressor
288 CFM at 125 psig
Operating range 95-105 psig
High pressure control air reciever tank design basis?
at 350 psig
-allows all valves to be stroked twice at a starting pressure of 260 psig assuming no compressor running
Instrument air compressor booster fan power supply?
Normally in auto
-runs when the compressor is running
FWP C-903A/B ratings/power supply?
Powered from LCC-91 (E bus)
876 SCFM at 125 psig
-normally use 50-100 SCFM
Cooled by non critical service water with a backup from the fire main
Auto starts at 95 psig when in auto (standby)
Instrument air post filters, F-5A/B, max D/P?
Purpose of the instrument air system?
Non safety related system that is required fo normal plant operations
-portions of the system are treated as safety-related
-containment isolation portion is safety related
-safety related control valves have N
Designed to provide a reliable source of dry, oil free air for instrumentation and controls, and service air
Design based on estimated consumption rate of 80 SCFM for nuclear steam supply steam and 115 SCFM for the remainder of the plant
High pressure air compressors, C-6A/B/C, ratings/power supplies?
22.3 scfm at 325 psig
NOP 310-325 psig
--MCC 8 (D)
--MCC 7 (C)
--MCC 4 (E)
Backup to T-9C high pressure air reciever tank?
Service air can supply T-9C via a temporary hose from an air bib
-must bleed off reciever tank pressure
Purpose of the service air system?
Non safety related system that provides unfiltered, undried air directly from the instrument air to service air hose stations and components throughout the plant
CV-1211 "Penetration MZ-65 instrument air containment isolation"
Provides isolation between instrument air and containment instrument air header
-handswitch in the CR
Fails open on a loss of air/loss of D-11
backup to allow closure
Instrument air compressor load/unload operation?
Load at 95 psig
Unload at 105 psig
If running unloaded for > 10 minutes
-compressor goes to sleep
-compressor will restart at < 95 psig
What must be done if T-9A lowers to < 260 psig in Modes 1,2,3 >/= 325
Tank shall be declared inoperable
The instrument air and N
supply to all CVs supplied by the inoperable tank shall be checked to ensure correct alignment
Review LCO 3.5.2. "ECCS-operating"
Instrument air compressor power supplies?
What must be done if T-9B lowers to <260 psig in Modes 1,2,3 >/= 325
Declare T-9B inoperable
Enter LCO 3.0.3.
Air bottle backup station
3 SCBA bottles connected to manifold to supply backup air to CV-0318 "P-66 discharge to HPSI train 2"
CV-1212 "Service air header isolation"
Isolates instrument air from service air
No handswitch, operates off of a pressure switch
Auto closes on 85 psig instrument air header pressure
Fails closed on loss of air/ DC bus D-11
Instrument air compressor trips
Load shed on loss of offsite power
-must restart compressor, doesn't sequence on
Various microprocessor alarms