Home > Preview
The flashcards below were created by user
on FreezingBlue Flashcards.
pressure reducing valves (PRV) only need to be installed when static line pressure in the water distribution system exceeds
585 kpa (85 psi)
Standard capacity PRVs are factory preset at..
344 kpa (50 psi) with adjustable pressure range from 172 kpa (25 psi) to 517 kpa (75 psi)
rotating disk meters are the most common household water meters. Tehy used for service pipe...
2" and less
style "3" meters, which come in sizes from....
1 1/2 " to 6"
turbine meters are good for a large flow of water and are frequently seen connected to the service for industrial pumps and equipment. this meter will not accurately register a flow rate below..
Compund meters are used with a water service larger than..
if a perfect vacuum could be created in a piping system, it would be possible to back siphon to a height of..
The principal causes of back siphonage are..
undersized piping 2 water main repair or break in the city or municipal water supply that is lower than a service point 3) lowered water main pressure due to high water withdrawl rate, such as fire fighting or water main flushing 4) reduced supply pressure on the suction side of a booster pump
the principle causes of back pressure are
- booster pumps
- potable water connections to boilers and other pressure systems
- interconnections with another system which operateds at higher pressure
- elevated piping, 9m 30' above finished grade
what should the size of an approved air gap be?
atleast twice the diameter of the inlet pipe, but never less than 25 mm or 1"
if if either check valve should leak, the differential pressure relief valve discharges water to the atmosphere to maintain a pressure differential of not less than..
14 kpa (2 psi)
any PVB that is 3" or larger has...
two check valves
An AVB is not normally installed more than _____ above floor level
1.2 m or 5'
what pressure is hot water tanks tested at?
what are the boiling points of water at the folowing pressures 14.7 pounds,, 50 pounds,, 100 pounds
212 f,, 297 f,, 337 f
standard temp and pressure releif valve settings are
temp releif = 99 c or 210 .... pressure relief 150 psi 1050 kpa
What would you like to do?
Home > Flashcards > Print Preview