Tech method lesson 1b.txt
Home > Preview
The flashcards below were created by user
on FreezingBlue Flashcards.
- author "me"
- tags "Cooling 101"
- description ""
- fileName "Tech method lesson 1b"
- freezingBlueDBID -1.0
- Subcooling measurement
- When you remove heat from a vapor, it condenses into a liquid.
- too much refrigerant in the high side will cause refrigerant to back up in the condenser limiting the ability of the condenser to reject heat.
- This quickly raises the condensing temperature and allows more time for the liquid too cool before reaching the outlet of the condenser.
- Resulting in high subcooling.
- The higher the subcooling the more refrigerant that is contained in the high side of the system.
- Some subcooling is required to ensure a steady flow of liquid to the metering device however too much will reduce the capacity of the condenser.
- Cold air flowing through the condenser coil increases its ability to reject heat and increases its capacity.
- Under cold ambient conditions it is necessary to simulate design ambient temperature by blocking off part of the coil to achive a condensing temperature of 100 - 110 degrees.
- Most gauges have both temperature and pressure scales get in the habit of reading the temperature instead of pressure think in terms of condensing temperature not head pressure.
- In most systems anything over 15 degrees subcooling is considered excessve consult the manufactures specifications.
- Excessive subcooling is caused by;
- Air or other noncondensables add pressure to the system without raising the temperature which distorts the pressure/temperature relationship.
- Pump the system down to ensure all the refrigerant is in the condenser coil then disable the compressor and run the outdoor fan till air in/out of the coil are the same when compare the pressure to a PT Chart if there is a higher pressure than the temperature (5 degrees) then there are non condensable in the system.
- Symtoms of non condensables in the system.
- Low side = normal side pressure and saturation temp. Normal superheat.
- high side = high discharge pressure, high subcooling
- If subcooling is high and the system does not contain non-condensable then we have excess refrigerant in the high side of the system.
- The system may be overcharged or the excess refrigerant has been borrowed form the low side (restriction)
- If the subcooling is excessive we must check superheat to dtermine if the system is over charged or restricted.
- Excessive subcooling with a high superheat would indicate a restriction.
- Xcessive subcoolng with a low superheat (fixed metering device) or normal superheat (txv) would indicate an over charge.
- Measure the air temperature entering the condenser and the air temperature leaving the condenser the difference should be no more than 20 degrees.
- The slower the air moves across the condenser coil the more time the air has to absorb heat.
- Dirty coil, improper fan blade or position in shroud, wrong RPM motor or wrong rotation motor.
High efficiency unit is not more than 15 degrees dfference.
What would you like to do?
Home > Flashcards > Print Preview