The flashcards below were created by user
on FreezingBlue Flashcards.
the disconnecting means for motors has 3 responsibilities. What are they? PP168
- To safely carry the load
- To be capable of being opened under load, and....
- To be capable of being opened under locked rotor conditions.
What indicates the locked rotor current of a disconnecting means? PP169
Can this horsepower rating be the same as the HP rating of the motor? Under what conditions? pp176
The horsepower rating of the disconnecting means
Yes: only when the code letter is between A and F
A design B energy efficient motor has a hi/ low starting current? PP169
The circuit breaker is/ is not allowed to be used as a disconnecting means for a motor? Why? PP 180
Is, becuase the UL directory lists them as having been tested for 6 times the devices rating and identified for such use per 430.109
The disconnecting means, versus the branch circuit rating, is rated at _______% of FLC of the motor plus heating loads? PP184
115%, versus 125% for branch circuits plus 125% of heating.
A molded case switch looks just like a molded case circuit breaker but is different how? PP 185
No overcurrent protection is built into it
For air-conditioning and refigerant equipment, the branch circuit selection current (BCSC) is always what in comparison to rated load current (RLC)? PP187
Section 440.32 requires the conductiors supplying a motor compressor to be 125% of the RLC or BCSC, _________. pp188
whichever is the larger